KUOYUH Overload protection Manufacturer
- PRODUCT DETAIL
Use ohmmeter for testing
1. If the overload protection device is disconnected, then let it cool to room temperature (closed) continue to measure.
2. Although capable of continuous observation of work overload, however, to confirm that the parts are there hard work according to specifications.
3. If you are not sure whether there is a problem overload, replace parts of the same
Motor overload protection device 88 series breakers UL / TUV / CE / CSA certific
Rated Current : 0.5A~30A
Rated Voltage : 125/250VAC 50VDC 50~60Hz
Open Capacity: 1,000A×125VAC
Hi-pot Test: 1,500V/min
Overload current : 10 times of rated current
Min voltage: less than 0.25V
Reset time : in 60 seconds
Insulation resistance : more than 500VDC × 100MΩ
Terminal temp : 100 % test under 25°C
temperature rise less than 25°C
Life test: 125VAC × 150 % current, over 500 cycles.
Test standard(25°C) of this circuit breaker:
100% rated current: No trip Off
150% rated current: trip off in 1 hour
200% rated current: trip off in 40 minutes
300% rated current: trip off in 10 seconds
Product Certification: UL / TUV / CE / CB / RoHS